International Withdrawal of BS921:1976 ? This old standard is being withdrawn on 1st Jan 2013 ( Standard number , BS 921: 1976 , Specification : Rubber mats for electrical purposes , status : WITHDRAWN ) as it conflicts with IEC61111:2009.
The direct Electrical Insulating Matting to replace BS921 is class 0 IEC 61111:2009 for working up to 1kV AC . For higher voltage , you may select higher classes 1 , 2 , 3 or 4 according to voltage resistance required.
A) Which product is the correct Electrical Insulating Rubber Matting for protection against electric shock risk ? B) Choose the correct class based on your overall voltage requirements. C) BS EN 61111:2009 ( IEC 61111:2009 ) is the latest standard for electrical insulating rubber matting in providing electrical protection by classes defined.
A) Product Name Model : GS-LV ( Low Voltage ) Corrugated Switchboard Matting / Non Conductive Switchboard Mat / Dielectric / Low Voltage Insulation Rubber Mat
B) Raw Material : NATURAL RUBBER ( NR ) BASE POLYMER ( Karet Alam )
C) Purpose Switchboard matting is a non-conductive high density rubber compound engineered to prevent electric shock around high voltage equipment. The non-conductive rubber compound creates an insulating barrier between the electrical source and ground.
D) Scope Our GS-LV is under IEC 61111:2009 Class 0 , Ideal for Dielectric Voltage / Withstand Voltage : 10,000 VAC and Recommended Maximum use Voltage : 1,000 VAC ( Low Voltage Switchboard Matting )
E) Characteristics 1) Brand : GSE Trade Mark : ( eRubber and Heat Insulation Mall™ ) 2) Model Name : GS-LV , Switchboard Matting / High Voltage Insulation Rubber Mat 3) Top Surface - Anti Slip Corrugated , with anti slip corrugated surface to provide safe working environment , pattern surface “grabs” the bottom of footwear, improving traction and safe from slippery . 4) Colour : Grey 5) Test Certificate : * provided 6) Product Compliance Status :-
A) BS EN 61111 Clause 184.108.40.206 Class 0 , Voltage Withstand Test
B) Comply to RoHS I & II , On 4th June 2015, Commission Directive (EU) 2015/863 was published in the Official Journal of the European Union (OJEU) to include the phthalates ( BBP, DBP, DEHP and DIBP, these are used to soften PVC and Vinyl ) into ANNEX II of the RoHS Recast Directive.
The new law restricts each phthalate to no more than 0.1% ( mg/kg = ppm ; 0.1wt% = 1,000ppm ) in each homogeneous material of an electrical product.
7) Specific gravity : ± 1.50 g/cm³ 8) Hardness : 60 ± 5 Shore A 9) Elongation : Min ± 250 % 10) Tensile Strength : Min ± 5 MPa
F) Specification 1) Nominal Thickness : 2.5mm 2) BS EN 61111 : 2009 Class 0 ( Withstood 10kV ) , GS-LV A) Model : GS-LV , Switchboard Matting, ( GREY colour ) , 2.5mm Tk x 915mm ( 3ft ) Width x 10,000mm ( 10 m ) Length / roll , 3) Weight / roll : Approximately > 30kgs / roll
"Authentic Mark “ 1) Trade Mark , defined standards and colour code labelling .
Karpet Panel Listrik / Non Conductive Switchboard Mat / Dielectric / High Voltage Insulation Rubber Mat Indonesia -- with Anti Slip ( Corrugated / Diamond Plate ) Top Surface
Disclaimer : * Note : Users need to evaluate suitability for their industries use ( applications ) before placing order from us . The Information provided on this website best advise our customers corresponds to current electrical matting standards . In the individual case it is the sole responsibility of the customer to evaluate requirements , in particular if specified properties are sufficient for use .
OUTER CARTON LABEL INDICATION :-
Non conductive Switchboard Mat / Dielectric / Low Voltage Insulation Rubber Mat :- Model : GS-LV( Low Voltage), Top Surface : Anti Slip Corrugated, IEC 61111: 2009 Class 0 , Dielectric Test Voltage : 10kV Nominal Maximum Use Voltage :1kV